Section Code 2043 : Incorporates a Type AB air gap backflow prevention arrangement upstream of washing and flushing function. The product incorporates a fluid category 5 backflow prevention arrangement.Back To Directory Sections
Closomat Asana Low Level WC suite incorporating a wall hung ceramic pan that is fitted with a douche arrangement. The cistern incorporates a side entry compact type float operated inlet valve and a drop type flush valve (dual flush of 6/4 litres) which is pneumatically operated by electronic or manual wall mounted push buttons. The cistern incorporates a type `AB` airgap (verified by test - suitable for backflow protection against fluid category 5) which feeds the douche arrangement. Maximum supply pressure 10.0 bar. Cold water use only.
Low Level WC suites incorporating a frame mounted ceramic pan that is fitted with a washing & drying arrangement which is fed via a type `AB` airgap (verified by test - suitable for backflow protection against fluid category 5). The cistern incorporates a side entry BS1212/4 float operated inlet valve and provides a type `AB` air gap. The drop type flush valve provides a single flush of 6 litres and is operated by elbow push button levers that are designed into the front of the cistern cover. Maximum working pressure 10.0 bar. Cold water use only