Section Code 0135 : Cold-water storage with cover or roof - plastic, sectional. Cisterns in this section are not suitable for water for domestic purposes unless they are so modified and installed as to comply in all respects with Schedule 2. Section 7, Paragraph 4, of the Water Supply (Water Fittings) Regulations 1999.Back To Directory Sections
`Sekisui` insulated or un-insulated sectional cisterns assembled from glass reinforced plastic (GRP) panels. The panels are constructed in sandwich form with a layer of GRP each side. The largest capacity cisterns have stainless steel internal bracing and UPVC (hollow) pole roof supports. The roof covers are of the same panel construction & panels with inspection hatch are provided. Joints are sealed with synthetic rubber gaskets. Cold water use only.
Range of GRP sectional storage cisterns and lids. The tanks are fitted with an air breather. Maximum working pressure 2.3 Bar. Cold water use only.
Range of hot pressed moulded GRP sectional cold water storage cisterns. Larger cisterns are fitted with PVC roof supports and are supplied with stainless steel ladders, tie rods, braces and hatches. Cold water use only.
M100 & M100-B30 ranges of hot press moulded GRP sectional, pre-insulated, cold water storage cisterns. The cisterns are sealed with butyl rubber and are supplied with a float operated valve (gunmetal or DZR brass body depending on size). The rooves are fitted with one or more sealed manhole access points, which can also be fitted at low level if required. Larger cisterns are fitted with stainless steel ties, GRP roof struts & GRP ladders. The M100-B30 models are supplied with a screened tank overflow, a screened tank breather, two-way expansion pipe tee piece, tank lid adaptor and tank connections. Models can also be supplied with access doors. Maximum working pressure of supplied inlet valve: Gunmetal body inlet valves 5.0 bar, DZR brass body inlet valves 10.0 bar. Cold water use only.